Payment & Shipping Terms:
|Name:||Malaysia Electric Powerful Steel Electrical Utility Poles With FRP 9m 7.2mm||Height:||9m|
|Port:||Always Shanghai||Galvanization Standard:||ASTM A123 Average Coating Thickness 86microns|
|Length Of Per Section:||Within 14m Once Forming Without Slip Joint||Welding:||AWS D1.1 Penetration :100%|
Malaysia Electric Powerful Steel Electrical Utility Poles With FRP 9m 7.2mm
1. Top diameter:120mm
2. Bottom diameter:225mm
5. Material:S355JR S275JR
|Design service||available,just offer design parameter|
|welding method||CO2 welding or submerged arc auto welding|
Raw material test → Cutting →Molding or bending →Welidng (longitudinal )→Dimension verify →Flange welding →Hole drilling →Calibration → Deburr→Galvanization or powder coating ,painting →Recalibration →Thread →Package
Because of the long and thin shape,closed polygonal section and apply of high strength steel material,these steel poles have excellent durability.they can withstand the extreme condition,such as the frost climate,unbalanced loads, or breaking of wire.
The designing weight of the steel poles are usually relatively light ,and is good for the operation,transportation,assemble and installation.
Since the long and thin straight line shape.the steel pole from Milkyway Steel Poles are easily intergrated into the landscape.At the protected areas(mountains),the installation of steel pole will not influence the aesthetic solution of the scenic spot.
The hot dip galvanization trearment can increase the service life of the steel polewithout the environmental pollution and no need for other daily maintance.The following described types are specially designed for Africa Market which can meet the regulated height and load standard of France electricity power company.
our steel pole is bend to form to the polygonal(conical) section firstly.Then it is welded by the automatic submerged-arc welding machine.Thirdly the top cap,strip and base plate will be welded to the pole.And finally other accessories (support brackets ,ladder support,etc.)will be welded to the pole shaft.
The galvanization of the steel pole are under strict control.galvanization is achieved by immersion in a molten zinc bath(450°) after pre-treated(dipping)
1. Remove all the equipment on the pole during Assembly.
2. Circle a sling around th epole shaft of each section.
3. Fix the sling on top section to one pulley block.
4. The sling on the bottom section is tightly fixed and fixed at the center of gravity.
5. Make the steel pole vertical by tighten the sling of the top section.
6. Fix the steel pole.
7. Remove the sling.